Innovation. Craftsmanship. Reliability.
Easy Terminations Of Service Entrance Conductors Before Utility Pad Mount Transformer Is Installed
- Ratings are 800 - 6000 amp 600 volt, 3 phase 4wire, 3 phase 3wire, and 1 phase 3wire, NEMA 1/3R dual rated and Isc ratings of 85KA RMS symmetrical with no cable lashing required. (Please contact factory for higher Ratings)
- Cabinets are free standing and suitable for indoor or outdoor applications.
- Cabinets are ETL listed and labeled as per UL 1773 termination boxes.
- Cabinets meet all Nema and NEC code standards.
- Cabinets provided with electrical grade plated Aluminum or optional plated Copper bus bars.
- Connectors can be provided as set screw style ranging from (1) #6-750kcmil or crimp style are available. (all connectors can be field installed or factory)